Subsequent Thermal Insulation of a 250-m³ Storage Tank with Energocell® Foam Glass Granules
Compaction along the collar was executed with hand-operated compaction tools, because of the space limitations and to protect the collar; but on the larger continuous surfaces electrical vibratory plates were used (because of the enclosed space). The applied compaction rate was 1:1.3, and the final 18-19 cm thick layer resulted from a 23-25-cm layer of loosely spread material. Granules of 10-60 mm fraction size, and fine granules of 4-8 mm were placed and compacted on this layer, to include them between the larger granules, and to level the surface - preparing it for the very high 13-tonne/m² load and the metal plating.
The 18-19-cm compacted Energocell® foam glass granule layer was then covered with 5 mm thick metal plates that were joined by continuous weld at their faying surfaces (on the photo only the temporary joins are visible).